I/O Wiring. PowerFlex 4M Quick Start Guide. Display. Parameter Group. First Shown when drive powered up. Display Group. (View Only). Basic Program Group. Allen-Bradley, Rockwell Automation, and PowerFlex are registered trademarks of PowerFlex 4M Adjustable Frequency Drive FRN – User Manual. View and Download ALLEN BRADLEY PowerFlex 4M user manual online. FRN 1 Series, FRN 2 Series, Adjustable Frequency AC Drive. PowerFlex 4M.
|Published (Last):||9 December 2012|
|PDF File Size:||8.42 Mb|
|ePub File Size:||14.39 Mb|
|Price:||Free* [*Free Regsitration Required]|
See Appendix B for ordering information. Page 30 Preset Frequency. Table of Contents Add to my manuals Add. User Manuals Wiring Diagrams. Press Enter or Sel to enter the group menu again. D-2 Connecting an RS Network. Page 22 When the AC line is removed, there will be a loss of any inherent regenerative braking effect that might be present – the motor will coast to a stop.
Drive will not power up without a jumper or inductor connected. Your browser does not support iframes.
Page 21 Drive will not power up without a jumper or inductor connected. Returns the same data as Reading 03 Parameter d [Output Freq]. Page 33 Installations on a public low voltage power network may require additional external harmonic mitigation. A valid start will override this command. Looking for Additional Information? Integral Keypad Scroll through groups and parameters. Caution should be used when enabling this feature, since the drive will attempt to issue its own start command based on user selected programming.
When the AC line is removed, there will be a loss of any inherent regenerative braking effect that might be present – the motor will coast to a stop.
See Appendix B for details.
Page 4 Description for option 21 of parameter t [Relay Out Sel] corrected. Basic Program Group A Stop drive before changing this parameter.
When this bit is a 1 btadley drive can be started. Page 58 Do not create a program that frequently uses configurable outputs to write parameter data to NVS unless C [Comm Write Mode] is set to option 1. Installations on a public low voltage power network may require additional external harmonic mitigation.
Application specific thermal considerations may require a larger enclosure. Catalog Number Explanation Page Figure B. Our Integrated Architecture Solutions provide the foundation to drive plantwide optimization efficiently and effectively, enabling you to respond competitively to the economy and changes in consumer demand.
Alternative resistors may be used, however care must be taken when making a selection. Page 97 Catalog Number: Press the Up Arrow or Down Arrow to scroll through the parameters in the group. Page 20 If it is necessary to disconnect power to the motor with the drive outputting power, an auxiliary contact should be used to simultaneously disable drive control run commands.
Values Default Drive Rated Amps 0.
Motor Ground The motor ground must be connected to one of the ground terminals on the drive. Each digital input draws 6 mA. Page 18 When using a Manual Self-Protected Type E Combination Motor Controller, the drive must be installed in a ventilated or non-ventilated enclosure with the minimum volume specified in this column.
Stop input also clears active fault. The integrity of all connections should be periodically checked. Safety Guidelines for the SGI In addition, some Modbus functions are supported to allow simple networking. Learn how the information from our portfolio of Intelligent Motor Control can position you to make better operating decisions, improve system performance, and gain operation efficiencies.
To print the manual completely, please, download it.
Page 32 Keep wire length as short as possible between the enclosure entry point and the EMI filter. Stops drive via coast to stop. Page of Go. Page 27 Direction Mode]. All drives must be powered up for the analog signal to be read correctly. An auxiliary braking method may brzdley required. Pull the cover out and up to release. To simplify drive setup, the most commonly programmed parameters are organized in a single Basic Program Group.
Page 40 Start Up Notes: Supplemental Drive Information Notes: Sets the time between restart attempts when A [Auto Rstrt Tries] is set to a value other than zero. Page 96 Catalog Numbers: Sets the frequency at which the drive will not operate.